CAN/ULC-S PERIODIC INSPECTIONS AND TEST – DAILY AND MONTHLY. NOTE: Refer to Appendix D for examples of Inspection and Test Record. SCOPE. This Standard provides requirements for the inspection and testing of fire alarm systems and specifies the devices and functions to be inspected. 1 SCOPE This Standard prescribes requirements for the inspection and testing of fire alarm systems and specifies the devices and functions.
|Published (Last):||13 July 2013|
|PDF File Size:||2.4 Mb|
|ePub File Size:||17.57 Mb|
|Price:||Free* [*Free Regsitration Required]|
CAN/ULC-S | Standards Council of Canada – Conseil canadien des normes
F Confirm that the alarm transmission to the fire signal receiving centre is received. Most house fires start in the electrical wiring so it’s a good idea to have a battery operated smoke alarm installed as a “back-up”. Y Ancillary device by-pass results in trouble signal. Indicate type of test performed on a fully charged battery select one: There are a total of: The printed maintenance and testing guide must be followed.
Maintenance Items Annually Hose nozzles – open and close and lubricate if necessary. Visual signal appliances individually inspected and tested.
If housing discolouration is noted, attempt to identify the source and note the date of manufacture.
CAN/ULC-S Fire Alarm Annual Inspection Test Form
Operation of the fire signal receiving centre transmitter bypass means results in a specific I trouble indication at the fire alarm control unit or transponder Operation of the fire signal receiving centre disconnect means transmits a trouble signal to J the fire signal receiving centre. Are above readings comparable to design values? Failure to flush yard piping or surrounding public mains following new installation or repairs? AA Fire alarm reset function operates.
In this instance the detectors are powered by a stand-by battery that will ensure continued protection even in the complete absence of electrical power or a “brown-out”.
Yes No Water Temperature: Backflow prevention assemblies shall be inspected locked or properly supervised by an acceptable electrical means. Documents Flashcards Grammar checker.
Description ca the function of each operating control and indicator on the fire alarm control unit. Individual alarm and supervisory input zone designation labels are properly identified.
Components of standpipe system inspected?
Standards Council of Canada
Interior of dry pipe valve cleaned? Minimum of one alarm zone and one supervisory zone tested per annunciator or sequential display to confirm operation. Is the building occupied? Seconds Are the results comparable to previous test? Engine hour clock reading: Is the building fully sprinklered?
CAN/ULC-S536-04 Fire Alarm Annual Inspection Test Form
The fire signal receiving centre is ULC Listed. Rated voltage is present.
Visual indicator test lamp test operates. Main drain test shall be conducted on each system riser. Smoke control installed in accordance with Measure: Confirm field device mechanically supported independently of the wiring. Magnetic door holder release activated by cna alarm system?
It’s also prone to false alarms when installed close to bathrooms or kitchens with older style dishwashers. Cap gaskets in place and in good condition? Foreign materials found in dry-pipe valves, check valves or pumps?
Alarm signal manual silence operates. The fire signal receiving centre transmitter is integral to the fire alarm control unit.